With Instructables you can share what you make with the world, and tap into an ever-growing community of creative experts.
We have a be nice comment policy. Please be positive and constructive.
We noticed you attached photosto your comment.
I had a water treatment plant out in the middle of BFE America. We tried some 10HP single phase 240v pumps and they just couldn't give a good reliability. The farmers electric coop wanted $27,000 to run 3 phase to the pumphouse. So, for the following 20 years, we ran a large box called a 3 phase emulator. It was basically a big box full of large a/c motor starters. It was solid state and worked quite well. It had one flaw we eventually fixed with a controller unit. If there was a lightning strike or other interruption in the 240v service, it shut down and would not restarted unless someone drove out and restarted it manually. We put in a special sensor box that would do a re-start on its own after a 5 minute wait. It would just keep restarting if there was a storm in the area. When that motor finally burned out enough where we could not rebuild it, we went with two, 10hp single phase 240v motors.
Installing a wind turbine to power my home!
How I built an electricity producing wind turbine
Hurricane Survival With a wind turbine
Windy The small Wind turbine
Wind generator with car alternator
Power Tower (plans) - electricity generation from solar, wind and water in one device
Seeing Green Energy - The Wind Turbine Myth
My Improvised DC Generator Build
Wind Generator Design #4
7 Foot Axial Flux Wind Turbine
Posted:Jan 30, 2009
Join 2 million + to receive instant inspiration in your inbox.
Download our apps!
© 2016 Autodesk, Inc.