They work well when new, but eventually fail and need to be replaced. Here's how to replace a GFCI outlet- or any outlet, really- or replace a standard outlet with a GFCI outlet.
Step 1: What You'll Need
- New GFCI outlet
- Insulated screwdriver
- Outlet tester
- Non-contact tester
- Electrician's pliers
All are inexpensive. The non-contact tester is used to see if a circuit is "hot"- that is, if there's voltage on it. The Outlet tester is used to make sure you've wired everything properly.
Step 2: Turn Off the Power!
Step 3: Remove the Faceplate
Step 4: Remove the Outlet
Step 5: Double Check the Power!
Notice that all the exposed connectors on this outlet are covered with a wrap of electrical tape- that's a good precaution whenever you install an outlet or switch. It helps prevent accidental shocks the next time someone services the box.
Step 6: Prepare the New Outlet
Here, I've grabbed the tab on the new outlet with my pliers, right next to the scored line. I'll bend each tab back and forth a few times and it'll snap right off.
Step 7: Wiring the New Outlet
The ground screw is connected to the ground wires coming and going to the box.
There are two sets of connectors for hot (black) and neutral (white) wires. One set, labeled LINE, is used for power coming in to the box, and the other, labeled LOAD, for outlets that will be "downstream" of the GFCI, and be protected by it. Make sure you know which is which- the old outlet will be labeled, as will the new.
If you can't see the markings on the old outlet, turn the power on briefly, and use your non-contact tester to find the hot wire- that's the one bringing power into the box. You'll connect that wire, and its white companion, to the LINE connectors. (And then turn the power off again.)
This GFCI outlet has both push-in and screw terminal connectors; some old timers (and some new-timers) will only use the screw terminals, but actually, the push-in connectors are more reliable, according to the GFCI makers.
Make sure the wires are stripped to the right length- there's a gauge right on the side of the outlet.
I've pushed the wires into the holes, tightened the screws, and put a couple wraps of tape around the outlet. Now it's time to reinstall.
Step 8: Replace the Outlet
Step 9: Replace the Coverplate and Test
Now plug in your circuit tester. You should see the two amber lights light up, but not the red light.
Push the test button. You should hear a snap, and all the lights will go out.
Push the reset button, and the amber lights should go back on again. If they did, congratulations. You're done.