I am an electronic engineer in the field of power distribution switches. In recent days, I am prepared to make a project for power distribution switches at home together. The project begins now: Home decoration, the concern of hydropower indispensable. The laying of the home circuit is a crucial link, the home distribution box installation involves the safety of home appliances. Therefore, I specifically summarise the home distribution box installation knowledge, as well as home distribution box wiring diagram to make the relevant finishing, for everyone to take precautions, the home distribution box has a clear understanding. Home distribution switch installation points 1, Household distribution switch sub-metal shell and plastic shell two, there are two kinds of mounted and concealed, the box must be intact. 2, The household distribution switch of the cabinet wiring assembly should be set up to zero line, to protect the ground wire, phase line, and to be intact, with good insulation. 3, The installation of air switch seat should be clean and there is enough space, should be installed in the dry, ventilated parts, and no obstruction, easy to use. Never install the distribution box in the box to prevent fire. 4, The household distribution switch should not be installed too high, the general installation of the elevation of 1.8 meters, in order to operate; into the distribution switch of the electric tube must be fixed with a lock nut. 5, If the household distribution switch to be open, the edge of the hole to be smooth, smooth, distribution box buried in the wall should be vertical, horizontal, edge left 5 to 6 mm gap, distribution box wiring Should be rules, neat, the terminal screws must be tightened. 6, The loop into the line must be sufficient length, no joints, after installation marked the name of the use of the circuit, the installation of household distribution box to be completed after the removal of the distribution box residue. How to assemble power distribution switches at home ? 1, The installation of electrical box, distribution box installed on the wall, should be used bolts (expansion bolts) fixed, bolt length is generally buried depth (75 ~ 150mm), the thickness of the box floor, nuts and washers Of the sum of the thickness, plus about 5mm of the "margin". For smaller distribution boxes, it is also possible to embed a good brick at the installation site (in the form of a distribution box or a panel mounting hole) and then use wood screws to secure the distribution box or power distribution board. 2, Dark assembly distribution box, distribution box embedded in the wall installation, in the wall when the hole should be reserved than the length and width of the distribution box about 20mm, the depth of the distribution of the thickness of the distribution box with the wall Plaster thickness. In the masonry distribution box, the box and the wall filled with concrete can be fixed to the box live 3, The distribution box should be installed firmly, horizontal and vertical, vertical deviation should not be greater than 3mm; concealed, the distribution box should be around the gap, the edge of the panel should be close to the wall, the box and the building, Part should be coated with anti-corrosion paint. 4, The distribution box installed in the spiral fuse, the power cord should be connected to the middle of the terminal contact, the load line should be connected to the threaded terminal. In this way, in the loading and unloading fuse will not be electric shock. Porcelain plug-in fuses should be mounted vertically. 5, The distribution box of AC, DC or different voltage levels of power, should have a clear sign. Lighting line, should be set to zero line (N line) and protect the zero line (PE line) bus, zero line and protection of the zero line should be connected to the bus, not twisted, should be numbered. 6, The wire leads to the panel, the panel line hole should be smooth without burrs, metal panels should be installed insulation protective cover. Metal shell distribution box shell must be reliable grounding (then zero). Ps: Excuse me if I was wrong in words or expressions as I am a green hand in the field of power distribution switches. I need continual learnings. What is your idea ? Do you agree with my ideas ? Any of your ideas would be highly appreciated. May someone would like to help ? thanks in advance.
Topic by maryzhu 2 years ago | last reply 2 years ago