If you stay in South Africa you would know that our beloved country is currently being run down by our government, But lets not get political :-)
ESKOM dubbed Eksdom is the sole power company in South Africa and is doing a real bad job at delivering power to its consumers and probably the only company asking consumers not to buy power from them , Weird hey!
So ESKOM has invented what they call load shedding, where by on a regualr basis power gets shut in areas right across the whole country , Except off coarse where the directors of ESKOM stays (Ok Just kidding , or wait is it true?) dont know but I dont doubt.
In my area loadshedding usually happens on Wednesdays at around 20:00 to 22:00.
I needed a solution that will allow me to watch TV and have internet during those hours. I found a couple of a old broke PC upses, the actual inverters were still fine just the 7ah internal batteries were dead.
Before I started I checked the voltage its using to charge the battery and it was charging at 13.54 volts, which was perfect because usually SLA (Solid Lead Acid) batteries usually start to gas at 14V and up also I noticed this charger maintains the battery by clicking a relay every now and again to top it up.
See the youtube video how i built it
1 X 102 A/h Deep Cycle Battery
1 X Broke UPS rated 460Watt
Soldering Iron to extend the UPS battery leads and some soldering wire.
Heavy gauge wiring kit
Teachers! Did you use this instructable in your classroom?
Add a Teacher Note to share how you incorporated it into your lesson.
Step 2: Take the UPS Apart
Open the UPS, In my case the UPS enclosure only had 4 screws holding it together and the front face just clipped off and I could remove a cable plug to separate the front button from the circuit board.
Immediatelyremove the battery terminals to prevent a potential lethal shock!
Step 3: Remove the Battery
Remove the battery, In this step's picture you can see the battery is swollen and its casing is cracked.
After removing it chuck it into the dustbin ( hehe only joking make sure you dispose of it correctly)
Step 4: Remove the Power Outage Buzzer.
Most UPSes have a buzzer to indicate its running on battery, this will drive you totally nuts and it will be very distracting.
the UPS is used also dims the front LED when its buzzing so I still have an indication to see when its running on battery as opposed to mains.
Not that it matters because I never have a load on this unless its load shedding, because when I'm at work and the power goes out during the day I dont want the UPS to power the TV, Internet or Decoder whilst not using it.
Step 5: Extend the Battery Terminals and Drill Holes in the Enclosure.
You need to extend the battery terminals so that you can hook it up to a bigger battery outside of the now dedicated inverter.
I stripped all the leads and extensions then twisted them tight and also soldered it, I went wild on the soldering, Note if the wires are to thin it will become hot and potentially be a fire hazard, be careful!
After that I drilled some holes and used grommets to fit the wires through.
And you are done with the inverter you can close it up.
Step 6: Build a Male Kettle Cord Lead
I used an old ordinary extension lead, cut off the 3 prong plug and soldered on a male kettle cord lead.
Usually this is the lead you plug into the PC and the other side into the UPS.
Step 7: Set It Up
I emptied one side of my TV cupboard then neatly stacked my battery and inverter next to each other, in the picture i'm only using one of the inverters seen in the picture, dont use 2 inverters off the battery.
Remember a battery also has a limit, just because it says it can deliver 100 Amps in an hour it doesnt mean you should or can draw that much, you will destroy your battery if you draw too much amps from it and will die quickly, Die not as in goes flat quick, die as in die buy a new one.
In this step I also show you how the max volts used to charge the battery,
Step 8: Important Notes
Make sure the inverter is double the wattage you are intending to run.
So add up everything you will be running from it then times that by 2.
For safety sakes, don't permanently use it as backup only plug things into it when you are there and need it.
Im drawing 110watts from this 102a/h battery and it will last 3 hours, if i draw around 200watts the battery leads become hot, BAD BAD BAD, So again for safety sakes dont run more than total 110watt appliances per 102a/h battery and you will be fine.
I would advise to check up on the battery water levels once every 3 or so months.
For crying out loud! DO NOT ACCIDENTALLY SWITCH THE POLARITY unless you like fireworks, mark the cables properly with Black and red , I used black insulation tape on the negative terminal.
If you have suggestions and notes to make let me know then I update this list.