So I decided to make my own grey water recycling system.
It is fairly easy to put together if you are technically minded. And doesnt cost to much compared to other systems.
Step 1: Basic Principle
here is a link to a larger image
Step 2: Parts Needed
1 x 40mm waste pipe.
3 x 40mm fitting for 110mm soil pipe
2 x end caps screw on type
1 one way valve
1 foam filter
1 storage tank with lid
2 ball cocks
Some 15mm copper or speed fix pipe.
2 reed proximity switches.
Originally I was going to use a 12 volt pump running from a solar panel. But the pump I had wasnt powerful enough to pump the water up to my loft so I had to use an old central heating pump I have from my old central heating.
Step 3: Assembling the Water Collection Pipes
You will need to make sure there is lots of adhesive on them and they are well sealed because there is quite a lot of pressure in the bottom of the pipes.
Then I drilled another 40mm hole in the top of one of the pipes so I could fit an overflow pipe.
Next I glued the screw on inspection end cap in the end of one of the tubes.
While the adhesive was drying I made up the cut off switch mechanism.
Step 4: Making the Cut Off Switch Mechanism in the Collector Tubes.
When the water level rises the ball cock pulls on the arm which moves the magnet against the side of the tube.
When the water level drops the arm drops back down and moves the arm away from the side of the pipe.
This I bolted to an end cap to be fitted in the bottom of one of the collection tubes.
With a 15mm fitting to supply water to the pump.
Step 5: Preparing the Storage Tank.
An over flow pipe. And a bull cock with a magnet attached.
And a reed switch which will cut of the power to the pump when the water level rises.
Step 6: Fitting the Pipes on the Wall
I bolted the two tubes together on the wall with a small peace of 40mm tube between them.
Then I fitted the over flow and the waste pipe from the bath to the top.
Making sure I had already installed the foam filter in the top of the pipe this is just held in place by chicken wire bent over the top of the pipe.
Step 7: Plumbing the System
which is connected to the central heating pump.
Then I ran some 15mm pipe up through the house to the top of the tank in the loft.
Then I attached the overflow pipe to the top of the tank and a 15mm pipe from the bottom of the storage tank to the toilet.
Step 8: Making the Control Box
So when the water level in the collection tubes drops to low the ball cock drop causing the arm to move away from the side of the tube. switching of the relay isolating the power to the pump.
The relay in the loft is off until the water level get towards the top of the tank. Then the magnet activates the switch causing the relay to switch on which will turn off the pump.
When the tanks are half full the circuit will switch on the pump and pump the water from the collection tube to the storage tank until ether the collection tubes empty or the storage tank is full.
Step 9: Wiring the Control Circuit and Pump.
Then I wired the pump up to the control box.
Step 10: Testing
I checked the tube for leaks if I found any I had to empty the water and apply more adhesive to the pipes to try and seal the leaks.
When the adhesive had dried I ran the test again to find any more leaks.
When I was satisfied there were no leaks I was able to test the rest of the system.
I switched on the pump and made sure there was no air in the system. And that the pump was powerful enough to pump the water to the tank in the loft. And checked that the loft tank was not leaking.
Then it was just a matter of waiting for the pump to pump enough water in to the loft tank so that the water level in the collection tubes droped enough to activate the switch and turn the pump off. At the same time I manually checked the switch on the storage tank would switch off the power to the pump when the water level rose to high.
When I was happy the switches were switching the pump on and off correctly.
And the pipes were not leaking and the overflow pipes were working correctly.
I put the lid on the loft tank.
And went and had a shower and allowed the water to fill the collection pipes, the pump switched on and the loft tank started to fill.
Then I just flushed the toilet to make sure it would fill up and there were no leaks.
And that was it.
Step 11: Update Fine Tuning
I have been using this grey water system for about 6 months now.
In this time I have had 1 or 2 small problems that I have had to sort out.
The first one is, I have had 2 switches fail. I have put this down to the switches not being able to cope with the current drawn by the relays so I have made a simple transistor circuit to reduce the current going through the switches this has also enabled me to use just 1 relay.
see attached circuit diagram.
the second problem has been when the weather gets hot there is a bit of a smell from the grey water stored in the tank in the loft.
I have calculated that the tank in the loft is holding to much water for to long.
It is holding enough water for 5 days. so I am replacing the tank in the loft with a smaller tank which will hold enough water for 1-2 days. then more of the water will be stored in the tubes outside. and the water will be recycled sooner. and won't be sitting around getting smelly.